Plate Heat Exchanger NORDIC Ba-16-34 1" 135kW
Plate Heat Exchanger / for heating and cooling technology systems
Model: NT Ba-16-34
Plate Q'ty: 34 pcs.
Connections: 1" BSP
Heat Exchange Area: 0.544m²
Heat Exchanger for boilers and fireplaces
Nordic Tec Ba-16-34
4x 1", 34 plates
- Heat Exchange Surface - 0.544 m²
In DOWNLOAD section you get the data sheet of the unit.
Sizing problem? Let us help and write us
Frequent Questions from readers - FAQ:
1. Is the plate heat exchanger insulation really needed? Can I do without it?
Answer: It is not mandatory, but if we want to have an effective heating system, it is recommended to use it. Without insulation, the exchanger acts like a small radiator - it reflects part of the heat outside. As a result of this - it heats the boiler room. This heat also comes from a heating boiler or a heat pump - so it's not for free and we'll have to pay for this.
Sometimes, however, the heating device is not in the boiler room, but e.g. in a garage where there is no heating and basically heat release by the exchanger is desirable to some extent. Then you can actually consider buying an exchanger without insulation, because we don't consider this heat loses as bad.
2. What is the maximum pressure that the Ba-16-34 heat exchanger can withstand?
The Ba-16-34 plate heat exchanger can withstand a maximum operating pressure of 20 bar. It has been tested with 2 times bigger pressure, this is a requirement of a producer during the tests of every single unit - but generally it's destinated for the systems with the pressure up to 2 MPa. This means it's not a gas or freon HE.
3. Is the Ba-16-34 heat exchanger suitable for use with high-temperature applications?
Yes, our PHEs and the model Ba-16-34 too, are designed to handle high-temperature applications up to 230 degrees Celsius. Of course those are the temperatures possible only in industrial applications.
4. How frequently should the Ba-16-34 heat exchanger by Nordic Tec be cleaned?
It is recommended to clean every plate heat exchanger at least once a year to ensure optimal performance for long years. However, the cleaning frequency may vary, it should depend on the specific installation and operating conditions. In fact neglecting the cleaning brings the result not so quickly, especially if the heat exchanger works in relatively new heating system and when it is correctly sized (which means a bit "oversized"). But in longer perspective not cleaned heat exchangers will work for less years than the cleaned ones.
You might also like